New York News
NYU Langone Medical Center to re-open Monday
NEW YORK -- NYU Langone Medical Center, one of two New York hospitals that had to evacuate patients at the height of the storm, said it would reopen Monday, although some doctors would see patients at alternate sites.
Seven backup generators at the hospital failed Monday night, forcing the evacuation of 300 patients.
At Bellevue Hospital Center, some 700 patients had to be evacuated after the power failed. An official there said the hospital could be out of commission at least two more weeks.
The closures led to dramatic scenes of doctors carrying patients down dark stairwells, nurses operating respirators by hand, and a bucket brigade of National Guard troops hauling fuel to rooftop generators in a vain attempt to keep the electricity on.
Both hospitals, NYU Langone Medical Center and Bellevue Hospital Center, were still trying to figure out exactly what led to the power failures, but the culprit appeared to be the most common type of flood damage there is: water in the basement.
While both hospitals put their generators on high floors where they could be protected in a flood, other critical components of the backup power system, such as fuel pumps and tanks, remained in basements just a block from the East River.
Both hospitals had fortified that equipment against floods within the past few years, but the water - which rushed with tremendous force - found a way in.
"This reveals to me that we have to be much more imaginative and detail-oriented in our planning to make sure hospitals are as resilient as they need to be," said Irwin Redlener, director of the National Center for Disaster Preparedness at Columbia University's Mailman School of Public Health.
The problem of unreliable backup electricity at hospitals is nothing new.
Over the first six months of the year, 23 percent of the hospitals inspected by the Joint Commission, a health care facility accreditation group, were found to be out of compliance with standards for backup power and lighting, according to a spokesman.
Power failures crippled New Orleans hospitals after Hurricane Katrina. The backup generator failed at a hospital in Stafford Springs, Conn., after the remnants of Hurricane Irene blew through the state in 2011. Hospitals in Houston were crippled when Tropical Storm Allison flooded their basements and knocked out electrical equipment in 2001.
When the Northeast was hit with a crippling blackout in 2003, the backup power at several of New York City's hospitals failed or performed poorly. Generators malfunctioned or overheated. Fuel ran out too quickly. Even where the backup systems worked, they provided electricity to only some parts of the hospital and left others in the dark.
Afterward, a mayoral task force recommended upgrading testing standards for generators and requiring backup plans for blood banks and health care facilities that provide dialysis treatment.
Alan Aviles, president of New York City's Health and Hospitals Corp., which operates Bellevue, said that after a scare last summer when Hurricane Irene threatened to cause flooding, Bellevue put its basement-level fuel pumps in flood-resistant chambers.
It still isn't clear whether water breached those defenses, but when an estimated 17 million gallons of water rushed through loading docks and into the hospital's 1-million-square-foot basement, the fuel feed to the generators stopped working. The floodwaters also knocked out the hospital's elevators.
For two days, National Guardsmen carried fuel to the generators, but conditions inside the hospital for patients and staff deteriorated anyway. The generators were designed to supply only 30 percent of the usual electrical load at the hospital, leaving a lot of equipment and labs hobbled. The hospital also lost all water pressure on Tuesday. Nearly 700 patients had been evacuated by Thursday afternoon.
"The precautions we had taken to date had served us well," Aviles said. "But Mother Nature can always up the stakes."
NYU Langone Medical Center had also tried to armor itself against floods.
All seven of the generators providing backup power to the parts of the hospital involved in patient care are only a few years old and are on higher floors. The fuel tank is in a watertight vault. New fuel pumps were installed just this year in a pump house upgraded to withstand a high flood, said the hospital's vice president of facilities operation, Richard Cohen.
"The medical center invested quite a bit of money to upgrade the facility," he said.
The pump house remained "bone dry," Cohen said. But water shoved aside plastic and plywood defenses and infiltrated the fuel vault, where sensors detected the potentially damaging liquid and shut the generators down. "The force of the surge that came in was unbelievable. It dislodged our additional protection and caused a breach of the vault as well," Cohen said.
The power at NYU went out in a flash, leaving the staff scrambling to evacuate 300 patients with no notice.
Dr. Robert Berg, an obstetrician, said that when he lost power in his apartment, he went to the hospital to charge his cellphone and was stunned to find it in chaos.
"It didn't really occur to me that the hospital was going to be in trouble," he said. Even after finding the lobby dark, "I thought, 'We'll have power upstairs. We're an operating room.'" He wound up carrying two patients down flights of stairs on a "med sled."
"There was a Category 1 outside and a Category 4 inside," he said. "I can't say that they were very well prepared for it."
That has left only one hospital, Beth Israel Medical Center, functioning in the southern third of Manhattan. It is also on backup power, but brought in two huge new generators Thursday, just in case.
NYU Langone Medical Center's Physician offices, and outpatient procedure and diagnostic testing sites will resume operation starting on Monday, November 5, 2012. Patients with previously scheduled appointments should call 866-724-1830 to confirm the location of their appointments.
The Hospital for Joint Diseases remains open and existing patients may contact the patient assistance line at 212-598-6336 for questions about services and appointments.
The Center for Muscuskelatal Care and the Clinical Cancer Center will also reopen on Monday, November 5, 2012.
Patients of the Clinical Cancer Center and the Stephen D. Hassenfeld Children's Center for Cancer and Blood Disorders who wish to reach their physician in the interim should call 800-400-8566.
New patients and new appointments may be scheduled starting Monday, November 5, 2012 through physician offices.
Additional information and ongoing updates can be found at www.med.nyu.edu.
Flooding may pose less of a danger to the hospital's power supply in the future. Construction is under way on a new power plant, at a cost of more than $200 million, that will run on natural gas and supply all the hospital's power needs.
"It's a tremendous facility, with a lot of hardening built into it," Cohen said.
Get Eyewitness News Delivered
new york city, hurricane sandy, new york news
- LIRR train derails in East River tunnel
- AccuWeather Forecast: Spotty Storm
- Live: Eyewitness News on 7online streamed live!
- WATCH ABC is available to Channel 7 viewers
- Victim of attempted robbery falls out window
- Suspect shot and killed in Newark robbery attempt
- Teacher suspended after alleged sending threatening voicemail
- Passenger arrested after incident on Newark-bound flight
- LI 7-Eleven owners accused of human smuggling
- NYC plans composting program to recycle food scraps
- abcnews: Murnaghans Face Backlash After Sarah's Lung...
- Actor Jeff Garlin won't face vandalism charges in LA
- Photos: Hong Kong-Newark Plane disturbance
- Photos: Miss Connecticut crowned Miss USA
Eyewitness News Links
Most Viewed StoriesMost Viewed VideoMost Viewed Photos